We use some essential cookies to make this website work.
We’d like to set additional cookies to understand how you use forestresearch.gov.uk, remember your settings and improve our services.
Preparing to search
Wood chips offer the advantage over logs that they can be fed automatically into a boiler. This makes them suitable for larger boilers, however they are a relatively bulky fuel so require a large fuel store.
Although logs can be stored and transported conveniently when stacked, and the ease of air passage through a log pile allows good drying, they are not suited to automated handling and feeding. Also, the relatively small surface area to volume ratiomakes efficient combustion or gasification difficult to achieve.
Wood chips can form a much more uniform fuel that can flow and can be fed to a boiler, gasifier or other conversion system as a steady flow using an auger feed or a conveyor. With a large surface area to volume ratio they can also be burned very efficiently.
Depending on the equipment they are to be used with, wood chips typically have a longest dimension from 20-50 mm, though larger chips (known as hog fuel), and chunks can be 100 mm or more. Long thin pieces (slivers) amongst the chips should be avoided as they can cause bridging and blockages in a chip feed system.
To produce chips suitable for most boilers requires a specialist chipper designed for woodfuel use to produce chips of even size that will flow well and ensure there are no long slivers that can cause jams or bridging. A general purpose chipper is not suitable.
Wood chips should be stored under cover to prevent wetting, however good airflow is necessary to disperse water vapour and minimize the chance of composting and mould formation.
In addition, stack height should be kept below 10 m to prevent heat build up from compostingand the potential forspontaneous combustion.
Wood chips may have a bulk energy density of about 40-50% of that of the solid wood.
Wood chips for energy applications should meet an appropriate quality standard if they are to be used reliably in combustion equipment, especially small scale and domestic equipment. Physical parameters, such as maximum size and absence of slivers or fines (sawdust), and maximum moisture content are important to allow reliable operation and prevent feed blockages. Also levels of contaminants and ash content will have an impact on emissions and maintenance schedules.
The British standards for solid biomass, including wood chips, allowall of these parameters, and acceptable ranges,to be defined.
The characteristics of wood chips will depend both on the chipper and the material from which they are made.They can be divided into groups:
Cookies are files saved on your phone, tablet or computer when you visit a website.
We use 3 types of cookie. You can choose which cookies you're happy for us to use.
These essential cookies do things like remember your progress through a form. They always need to be on.
We use Google Analytics to measure how you use the website so we can improve it based on user needs. Google Analytics sets cookies that store anonymised information about: how you got to the site the pages you visit on forestresearch.gov.uk and how long you spend on each page what you click on while you're visiting the site
Some forestresearch.gov.uk pages may contain content from other sites, like YouTube or Flickr, which may set their own cookies. These sites are sometimes called ‘third party’ services. This tells us how many people are seeing the content and whether it’s useful.